Are you looking for Benson boiler? So, Today we will study the Construction, Working, Advantages, Disadvantages, Application of Benson Boiler. Before going into details I must say, here you will get the articles of Mechanical Engineering in Brief with Some Key Points and you will get to know an enormous amount of knowledge from It. So if you find helpful this articles, please let us know in the comment box either if any correction required too, also let us know in the comment box.
What is Boiler:
- A boiler is a closed vessel in which fluid (generally water) is heated up to high-pressure steam. The boilers are used in power plants, for the generation of steam.
- They are mostly used in the power plants where steam turbines are used for the generation of electricity.
There are two types of boiler:
- Fire tube boiler
- Water tube boiler
Fire Tube Boiler:
- Fire tube boiler is those boiler in which the fire or hot gas is present inside the tubes and water surrounds these fire tubes.
- Since fire is inside the tubes and hence it is named as fire tube boiler. The heat from the hot gases is conducted through the walls of the tube to the water.
- The examples of the fire tube boiler are the simple vertical boiler, Cochran boiler, Lancashire boiler, Cornish boiler, Locomotive boiler, Scotch marine boiler and Velcon boiler. and whereas,
Water tube boiler:
- Water tube boiler is those boiler in which the water is present inside the tubes and fire or hot gases surrounds these fire tubes.
- The examples of water tube boilers are a La-Mont boiler, Benson boiler, Stirling boiler, Babcock and Wilcox boiler, Yarrow boiler and Loeffler boiler.
Construction of Benson Boiler:
This boiler has a unique characteristic of an absence of steam separating drum. The entire process of heating, steam generation, and superheating are done in a single continuous tube.
The feed water by means of the feed pump is circulated through the economizer tubes. Hot flue gases pass over the economizer tubes and the feed water is preheated.
Radiant evaporator–The feed water from the economizer flows into the radiant evaporator with radiant parallel tube sections. The radiant evaporator receives heat from the burning fuel through the radiation process and the majority of water is converted into steam in it.
The remaining water is evaporated in the convection evaporator, absorbing the heat from the hot gases by convection. Thus the saturated high-pressure steam at a pressure of 210 kg/sq.cm is produced.
The saturated steam is now passed through the convection superheater where the saturated steam os superheated to 650’C. The radiant evaporator, the convection evaporator, and the convection superheater are all arranged in the path of the flue gases.
Related Articles: Lamont Boiler working principle with Diagram
The superheated steam is supplied to the steam turbine through the steam outlet.
The capacity of Benson boiler is about 150 tonnes/hr at a pressure of 210 (kg force per square centimeter). and at a temperature of 650ºC.
- It works on the pressure of the water which is increased to the supercritical pressure (i.e. above the critical pressure of 225 bar).
- When the pressure of water is increased to the supercritical level, the latent heat of water becomes zero and due to this, it directly changes into steam without boiling. And this prevents the formation of bubbles at tube surface.
- In Benson Boiler, the feed pump increases the pressure of the water to the supercritical pressure and then it enters into the economizer.
- From economizer, the water the water passes to the radiant heater.
- Here the water receives the heat through radiation and partly gets
converted into steam.
- The temperature raises almost to the supercritical temperature.
- After that mixture of steam and water enters into the convective evaporator where it is completely converted into steam and may superheat to some degree.
- Finally, it is passed through the superheater to obtained the desired superheated steam.
- This superheated steam is then used by turbines or engine to produce the electricity.
- Advantages, Disadvantages, And Application Of Fire Tube Boiler
- Advantages, Disadvantages, and Application of water tube Boiler
The advantages of Benson Boiler:
- It is lightweight and it has no drum. For this reason, it is lighter than others boiler.
- It starting time is less than others boiler and
- it has up to 90 percent thermal efficiency.
- Due to supercritical types of boiler, its controlling need to monitor every time for preventing an explosion.
- Boiler control for the variable load is difficult.
Application of Benson Boiler:
- This supercritical boiler is used in different industries to generate steam for the production of electricity or mechanical power.
- The average operating pressure, temperature, and capacity of Benson boiler is 650 degree Celsius, 250 bar, and 135 tonnes/h.
- In Benson boiler, there are no drums, so the total weight of Benson boiler is 20% less than the other boilers. that reduces the cost of the boilers.
- Because of no drums are used in this boiler, the transfer of the Benson boiler parts is easy. chances of all the parts may be carried to the site, without pre-assembly.
- One more feature this is a once-through boiler and the feed water entering at one end is discharged as superheated steam at the other end.
Today we have learned about Construction, working, Advantages, Disadvantages, And Application Of Benson Boiler. If I have missed some, kindly inform me through commenting. If you like this article, don’t forget to share it on social networks. Subscribe our website for more informative articles. Thanks for reading it. Thank you.